Identifying power terminal lug data for the D2 style contactors
Tesys D line contactors
Products sold and used in the United States
Power terminal lug data required
For contactors with screw clamp terminals:
stranded cable w/o cable end : One #10-3 AWG or Two #10-4 AWG per terminal.
stranded cable w/cable end: One #10-4 AWG or Two #12-2 AWG per terminal.
solid cable: One #10-3 AWG or Two #10-6 AWG per terminal.