Frequently Asked Questions
Coil consumption or burden for the Tesys LC1D/2D contactors from 9A - 38A
Contactors and Starters - IEC
Tesys D Contactors
All AC coils for the LC1D09 through LC1D38 3-pole contactors ( including ring tongue, quick connect and spring terminal versions ) have an inrush of 70 volt-amps for either 50 or 60 Hertz applications, and a sealed value of 7 volt-amps for 50Hertz applications or 7.5 volt-amps for 60 Hertz applications.
No we don't. The closest we get is the 238A/25 with one 25 entry on the top.
With 9001KP38 and 9001A6 together will be the replacement for the 9001KP38A9.
How do we access the coil in the 9-38A rated D line contactor for replacement or inspection?
TeSys D line contactors
9-38A TeSys D line contactors
In order to access the AC coil you will need to use a small screw driver to press in the tabs located halfway down the top and bottom of the contactor. This will release the back of the contactor so that you can remove the old AC coil and insert the new coil.
DC coils are not serviceable. TeSys D line contactors with DC coils must be disposed properly in accordance with End-of-Life documentation found here:
AC Coil Replacement Instructional Video:
DC Coil End-Of-Life Video: