No, we don't have an offer for the socket
Not suitable for use over 75 degrees C
No, but a PRA90039 is the least costly lock, supplied with 2 x 405 keys.
Part number PDL565BK is obsolete in Black only available in white
Overall dimension of 651A2-BK is 365 (W) x 209 (H) x138(D).
The 265 Series of adaptable boxes is IP56 rated. Each box is supplied with a 3mm sealing gasket.
No the largest is the 100A which has a part code is PDL 765
Customers need to correctly identify a 'U-space' or 'rack space.'
All versions and serial ranges.
Incorrect placement of equipment can create airflow problems, like hot air recirculation.
Resolution: see below
As set forth by the EIA/ECA-310-E Standard:
1. For any Rackmount device or enclosure - a U or unit of rack space is equivalent to 1.75 inches or 44.45 mm.
2. The mounting hole pattern on a rack or enclosure must follow the following guideline:
- Vertical Hole spacing must follow a pattern of 5/8""-5/8""-1/2"" or 15.9mm-15.9mm-12.7mm
- Horizontal Hole spacing must be 18.3"" or 465 mm (+/- 1.6 mm)
- Clearance between inner edges of mounting rails must be 450 mm at minimum
- Outside edges of mounting rail must be 483.4 mm apart at minimum
EIA/ECA-310-E rail specifications in attached file.
To properly mount a device in the rack, a user needs to utilize the notched
square mounting hole to indicate the center of a U space. For Example, to mount a 1 U device, 3 mounting holes would be covered by the device with the notched hole residing in the center of the group of 3. Mounting in an "off-U position", effectively moving the installed device 1 hole space up or down is incorrect and will lead to airflow and cooling issues.
No , There is currently no replacement RCD available for the 485 series.
For more information on the 485 series please visit the Clipsal Website on the below Link
No, but you can use the PDL 56 Series 56AI310 and 56CSC310
The replacement will require two parts:
- ZB4BG0- Keyed 455 Selector switch
- ZB4BZ103- 2 N/O contacts + Mounting collar
You can use the 265 Series eg. Part 265/1-GY
User wishes to know how differential protection is calculated for VAMP 265 relay
VAMP 200 series
Differential protection stage in VAMP 265 is calculated based on fundamental frequency phasors which are calculated using discrete Fourier transforms (DFT).
The sampling rate is 32 samples per cycle and the DFT sampling window width is one cycle.
The fundamental frequency current phasors are calculated every ten milliseconds.
The part number for the screws would be 265SCREW.
The pressure switch with 435 - 7250 psi is actually piston actuated, therefore we do not have a replacement diaphragm for it.
The 265 series is a range of IP56 rated insulated boxes suitable for numerous junctions and terminations. Each box is supplied with a 3mm sealing gasket.
This applies to the 265/1, 265/3, 265/4, 265/5, 265/7 and 265/7D.
The replacement for the LC1D1810 at 415 volt is the LC1D18N7.....comes with 1 N/O and 1 N/C auxiliary already fitted as standard.
405 Key + Lock for enclosure NSYPLM64B = NSYTL405PLM.
The part numbers are the 4EBE210/30 and 4EBE210/10 - these are no longer available to purchase but are still being used within the 485 range of portable outlets.
They are not available as spare parts. The 485 series is currently undergoing a redesign to move away from these parts but is not yet complete. This redesign will use a standard part again.
Either a 435 which isnt water proof or a 56AI310
A customer would like to know if PME 8.x is compatible with MS Office 365.
Currently PME 8.x supports Excel 2016 which is part of Office 365. This is strictly in the sense that Excel 2016 is installed locally on the server or engineering client in order to run reports. The cloud based components of 365 are not supported.
Yes, the TSXCUSB485 can be used to connect to the LXM28 but only connect pin 4/5 and 8.
The PDL 58 is obsolete, there is no direct replacement.
Issue: Why will the Altivar ATV16 not run when set up for local mode?
Product Line: ATV16
Cause: Not running in local
Resolution: Verify Fwd command and correct switch positions as well as verify reference frequency. Need to set LFr to the required setting.
Issue: Where would you wire in an emergency stop on the Altivar ATV18.
Product Line: ATV18
Resolution: Can put it between LI1 forward and +24 since will only be running in forward direction.
30VA In Rush
4.5 VA Sealed
,What is the Schneider recommended part number for an output filter for a 60 horsepower 460 volts motor?
60 HP/ 460 volts output filters
1 - Product Selection & Services
One option is a ZB4BG212. This has a 421E key.
Issue: Need to know the operating voltage of the Vamp 255 digital inputs.
Product Line: Vamp 255
Resolution: The Vamp 255 has 2 sets of digital inputs. Digital inputs 1-6 are internally wetted with 48Vdc. The other 12 digital inputs operating voltage is defined by the part number ordering code:
A = 40 - 265 VAC/VDC
B = 18 - 36 VDC
C = 40 - 265 VAC/VDC + ARC Protection
D = 18 - 36 VDC + ARC Protection
E = 40 - 265 VAC/VDC + D19, DI20 + ARC channel
F = 18 - 36 VDC + D19, DI20 + ARC channel
Keywords: Vamp 255, Vamp 255 digital inputs, Vamp 255 operating voltage
no unfortunately. however we do offer a 435 but that does not have an IP rating. if you need an IP rating you can use the 56AI310 which is a 56 series apliance inlet rated to 10 A and has an IP rating of IP56.
Is it possible to change the current sensors inside of the Masterpact NT or NW breakers?
Masterpact NW NT
No, the current sensors or CT's are embedded inside the sealed case and not replaceable.
Dead error 405 is defined as "time out waiting for Modbus Plus"
Sub code 81 means "Prom Checksum error"
During operation the MB+ processor periodically performs self tests. This error means that the computed checksum was bad.
What are the dimensions of the Enercept Network Adapter 485 (ENA 485)?
Enercept Network Adapter
User would like to know the dimensions of the Enercept Network Adapter
Installing Enercept Network Adapter
Enercept Network Adapter dimensions are: 3.75 inches long, 1.5 inches wide and about 2 inches deep to compensate for the connectors and wiring.
No, unfortunately the WIBM550R is no longer available.
The replacement is the 56AI550
Some of the key features are:
- 5 round pins
- 204 mm Height x 101 mm Width x 165 mm Depth
- 10 - 16 mm conductor terminal
For further information please visit https://www.clipsal.com/Trade/search-results?q=56ai550
I have an LC1D TeSys D-Line contactor. Which are the coil terminals?
D Line contactors.
Products sold in the United States.
The coil terminals are the ones labelled A1 and A2.
CTA-ID : 2011973
Spare parts for the ATS46.
All models and serial numbers
Schneider Electric does not provide the control transformers as a spare part for the ATS46 soft start.
Would suggest to replace with a ATS48 soft start
What are some major differences between M-flex, E-flex, S-Flex and Field Drives?
EFlex, MFlex and Field Irrigation
E-Flex AC drives are packaged, adjustable speed drive solutions for commercial and industrial pump and fan applications. It offers a full range of E-Flex drives to meet specific indoor and outdoor applications
Type 1 enclosure for indoor, non-dusty environments
Type 12K enclosure for indoor, dusty/wet environments
Type 3R enclosure for outdoor, rain or shine environments
1 - 100 HP variable torque 460 VAC, three-phase input
1 - 50 HP variable torque 208/230 VAC, three-phase input (10° to 50°C ambient temperatures)
The S-Flex 212 enclosed drive provides the right features for HVAC pump fan applications.
Available in a NEMA Type 1 enclosure only.
460 Vac Three Phase / 1 - 100 HP
208/230 Vac Three Phase / 1 - 40 HP
The M-Flex™ enclosed drive featuring either the Altivar® 61 or Altivar 71 drives within a Type 1 general purpose or Type 12/12K drip/dust proof enclosure in integrated or barriered designs. M-Flex enclosed drive controllers are low voltage products available in the following ratings:
Altivar® 71 power converter
1 to 450 hp, 460 V
1 to 40 hp, 208/230 V
Variable torque (Light duty, 110% current limit)
Altivar 61 power converter
1 to 500 hp, 460 V
1 to 50 hp, 208/230 V
The Field Drive package is a sealed Type 3R enclosure package that completely isolates all the critical internal electronic components from the outdoor elements.
Oil & Gas
Constant torque (Heavy duty, 150% current limit)
Altivar® 71 power converter
1 to 600 hp, 460 V
1 to 100 hp, 230 V
Variable torque (Standard duty, 110% current limit)
Altivar 61 power converter
1 to 700 hp, 460 V
1 to 125 hp, 230 V Available Ratings
1 to 600 hp, 460 V
Depending on what the safety requirements are there are a few options.
ASISEK1C for AS-i systems
XALK188F has 2 x N/C contacts for standard wiring
Both are enclosed but parts can be supplied.