Frequently Asked Questions
Use PDL 100MPIR + PDL 600RM relay
IEEE 519 is recommended practice standard and not really mandatory; Utility may ask this to be enforced;
Use the PDL 100MPIR + 600RM if required to switch higher loads
This does not have a manual override, you would need to use the 648TM with a 600RM in order to get that functionality
The 173SS is rated at 316 Grade Steel
Can you connect 24vdc or 120vac to the start terminals 5-6 on the S-flex?
Altivar ATV21 or ATV212 S-flex enclosed
They have a start command with voltage and want to know if they can put it on the start terminals 5-6.
We only recommend that you put a dry contact between terminals 5-6 for the start command. We are supplying the 120vac power to these terminals. Please do not bring your own voltage into there terminals.